Installing a two-step purification of circulating water cooling
As part of modernization to increase the service life of the compressor shaft seal, introduced in February 2012 in the operation of the plant hydro promptly carried out the design, manufacture and delivery of a comprehensive two-step filter system cleaning cooling circulating water.
The filter installation is designed to remove from the stream of recycled water solids and suspended solids from the filtration of 100 ratings and 10 microns, and is currently commissioned.
|Material||steel 09G2S, 20|
|Wall thickness, mm||8|
|Designer and supplier||JSC «ЕС «Technohim»|
|Pressure design, MPa||1,6|
|Temperature design, °C||+50|
|Filtration rating, µm||100, 10|
|Project implementation period||20 calendar days|