The main purpose:
- reducing the pressure of the fluid or gas to the required process parameters.
The main equipment
- pressure regulators.
Depending on the equipment used by different pressure regulators control method and can maintain pressure.
The operating principle of pressure regulators are divided:
- regulators of direct action and indirect controls;
- discontinuous and continuous.
The controller direct regulatory authority is under the control parameter either directly or through a dependent parameter.
The controller indirect sensing element acts on the regulator outsiders independent source of energy that can be air, gas, liquid, and so on.
Both types of regulators consist of a valve sensitive (measurement) and control elements.
Number of pressure regulators is determined by the operating conditions of the equipment for maintaining the desired pressure, as well as according to customer requirements.
- petroleum and petroleum products
- associated petroleum gas
- liquefied petroleum gases
- liquefied natural gas
- flammable liquids
- combustible liquids
- nonaggressive environments
- aggressive environment
Pressure: from 0,07 MPa to 25 MPa.
Temperature, °С: from -196 up to 350.
Electrical power system
Category reliability of power supply — I.
Supply voltage 380/220V, 12V lighting repair.
System of grounding TN-S.
Automatic switches conform to requirements of industrial safety of the Russian Federation.
On the object provides the following types of coverage:
- working lighting — 220V;
- emergency lighting — 220V;
- repair lighting — 12V (apply reducing isolation transformers 220/12V);
Electrical safety system
Electrical Grounding is made in accordance with the requirements of industrial safety of the Russian Federation.
To protect people from electric shock in the building all metal fine dead parts of electrical equipment are grounded in accordance with the requirements of industrial safety and also the system of equalizing of potentials is carried out.
The temperature of the indoor air block must comply with the technical requirements of the manufacturers of the equipment, systems, devices and instruments, but not less than +5°C and above +35°C .
Heating chamber block can be formed as by electrical heaters and water by means of heating.
The ventilation system is performed in accordance with the requirements of industrial safety of the Russian Federation.
Automatic Fire Suppression
The unit has the following performance:
- fire suppression contains the estimated amount of extinguishing agent available for immediate use in the event of a fire;
- installation supplies at least 95% of the estimated mass of extinguishing agent required to create a fire extinguishing concentration in the protected area, designed to extinguish a fire in a time not exceeding the normative;
- installation provides a delay of release of fire extinguishing substance to the protected placements on time;
- installation is automatic and remote starter types.
Gas contamination monitoring system
Gas contamination monitoring system consists of a secondary device and field sensors for the corresponding gas.
Gas contamination monitoring system is provided with the necessary number of sensors, taking into account the composition of the target gas (vapor).
The control device includes a measuring apparatus for displaying the current gas concentration for each sensor.
The device should have a lock function alarm and re-install.
Completeness of delivery units is determined by the specifications for the contract.
The scope of supply may include:
- block-box type container;
- technical equipment (mobile devices, lifting gear, etc.);
- technological equipment (main and auxiliary);
- electrical power system;
- lighting system;
- electrical system;
- heating system (water/electric);
- ventilation system (operating, emergency);
- automatic fire extinguishing system;
- gas contamination monitoring system;
- system light and sound alarm;
- supporting steel structures (stairs, catwalks, fences, etc.);
- flanges, plugs, gaskets, fasteners for all flange connections;
- welding consumables for welding in the installation;
- shutoff and control valves, control instrumentation and automation;
- corrosion and coatings for painting after installation;
- insulating materials;
- the technical documentation.
In coordination with the Customer in specifications other completeness of delivery can be defined.
The technical documentation includes:
- assembly drawing of the technological block;
- drawings of assembly units;
- assembly drawing;
- installation and operation guide;
- calculation (if necessary);
- shipping documentation.
The passport is made out and signed by responsible persons of the enterprise of the producer (supplier) of the technological block.
Structure of the equipment is not limited to the following list, to be specified and may vary when considering the requirements of the customer and meets the specifications applied to the documentation.
The passport and the technical documentation which is its part is transferred to the Customer no later than 30 days from the moment of completion of works on assembly and installation of the technological block on object of the Customer.
Shipping documentation is sent to the Customer together with the equipment supplied.
Permitted by agreement with the customer sending shipping documents by mail within 15 days from the date of shipment of the equipment and its components.